May be used as service-entrance conductors and in other applications where SE cables are permitted when installed as specified by NEC® Article 230. May be used in dry, above-ground applications only at temperatures up to 90°C.
Type XHHW-2 conductors
Black XLP (cross-linked polyethylene), rated 90°C in wet or dry locations
Polarity ID: A red stripe on one conductor’s insulation surface
UL® 44 (insulated conductors)
UL® 854 Service Entrance Cables
Federal Specification A-A-59544
NFPA70: National Electrical Code®
Insulated and bare conductors are twisted together.
A glass-reinforced tape is applied over the conductors.
|Product Code Number
Explain Product Codes
|AWG Size||Bare Equipment Ground AWG||Approx. O.D. Inches||75°C****||90°C****||Dwelling*****||Approx. Net Wt. Lbs./M Ft.|
*Per Table 310-16 NEC®
**For termination to equipment for circuits rated 100 amperes or less or marked for Nos. 6 through 1 conductors.
***For termination to equipment for circuits rated over 100 amperes or marked for conductors larger than No. 1.
*****For dwelling units, conductors shall be permitted at listed ampacities for 120/240 colt, 3-wire, single-phase service conductors that supply the total load.